With a Thermal Tech blanket insulation encased between dual walls, DuraTech offers the optimum in safety and performance. It keeps the outer wall of the chimney cool, while ensuring high flue gas temperatures for optimum draft performance.
The inner wall is 25% thicker than competitive chimneys for an extra margin of safety. No locking bands or mechanical fasteners required.
DuraTech’s sleek 1″ wall design provides for easy installations through 16″ on-center framing. For tight installations, a Reduced Clearance Square Ceiling Support Box is available (6″ diameter DuraTech only).
Designed for normal, continuous operation at 1000°F flue gas temperatures, DuraTech is subjected to rigorous and stringent high temperature requirements of the UL standard, including one hour at 1400°F, plus three ten-minute chimney fire test at 2100°F.
5″-8″ DuraTech is a double-wall, all-fuel chimney system for use with wood stoves, fireplaces, furnaces, boilers, ranges, water heaters, or other appliances fueled by wood, oil, coal, or gas, and zero-clearance fireplaces that are factory-built.
Materials and Construction
5”-8” diameter pipe features inner wall of .020” 430 stainless steel. Outer wall options of .016” 430 stainless steel or .021” galvalume steel.
A Thermal Tech (ceramic refractory) blanket insulation is encased between walls. Stainless steel end rings seal the pipe.
DuraTech features light weight insulation, twist-lock fittings, support boxes with factory installed starter sections, elbows with 360° swivel base, select black finish pipe lengths, and five foot length pipe sections.
2″ clearance to combustibles.
UL Listed with DuraVent shroud specifications. Information available online at www.duravent.com or call and request L150.
c-UL-us Listed to UL 103 HT and ULC S604 (MH7399) (Stainless steel outer wall required for installation in Canada.)
Refer to our Typical Installation drawings to select the appropriate component parts for your installation.
- DVL/DuraBlack Chimney Adapter must be used when connecting DVL pipe to a Ceiling Support Box or Finishing Collar. When connecting DuraBlack pipe, a DVL pipe to a Ceiling Adapter, DuraBlack Slip Connector, or Snap-Lock Adapter must be used.
- Wall Thimble must be installed with an appropriate length of chimney pipe for all horizontal through-the-wall installations. To accommodate thicker walls, the telescoping pieces of the Wall Thimble can be separated, and a field-fabricated extension may be installed.
- Attic Insulation Shield must be used in all installations that pass through an attic, regardless of whether the attic is insulated or not.
- Firestop Radiation Shield must be used when a chimney passes through a floor or ceiling without a support box.
More Typical Installations:
|1||DVL or DuraBlack|
|5||Attic Insulation Shield|
|11||Tee with Tee Cap|
|13||Chase Top Flashing|
|14||Base Tee/Double Tee|
|15||Anchor Plate or Anchor Plate with Damper|
|18||DVL Adapter, DuraBlack Slip Connector, or Snap-Lock Adapter|
Planning Your Installation:
The following recommendations are general guideline to assist in the layout and selection of the chimney components needed for your installation. Always follow DuraVent Installation instructions before installing your chimney system., found with the cap or support box.
- The diameter of the chimney should match the outlet size of the appliance. An improperly sized chimney results in poor draft and excessive creosote formation.
- Measure the diameter of the appliance flue outlet. Select the chimney and either DVL or DuraBlack connector stovepipe with the same size diameter as the appliance flue outlet. For fireplace installations, refer to the sizing chart in the back of this catalog.
- Determine if the installation is a through-the-roof installation or a through-the-wall installation. A through-the-wall installation will require additional components (Wall Thimble, Tee/ Cap, Tee Support, and Wall Straps).
- Install the chimney in the interior of the structure whenever possible. A cold exterior chimney will produce less draft and will generate more creosote.
- If possible avoid offsets that serve to restrict the natural draft. A straight vertical installation is more efficient and less likely to develop creosote. If an offset is required to avoid rafters or other obstructions, measure the horizontal distance required and the vertical height available. Both 15° and 30° elbows are available. Elbows have a 360° swivel base to allow orientation of elbow direction only. Elbows are fixed at 15° or 30°. Elbows greater than 30° are not allowed in the United States. A maximum of two offsets in a single installation are permitted. Refer to the offset table in the back section of this catalog. At least one Elbow Strap is required for each offset. Elbow Straps ensure adequate support.
- Determine the minimum chimney height above the roof line. Building codes require a minimum of 3′ above the roof penetration and at least 2′ higher than any portion of a building within 10′. See figure 1. The termination cap is installed above that point. If chimney extends 5′ or more above the roof penetration an extended roof bracket is required. An additional roof bracket is needed every 5′.
- Measure the roof pitch. For example a 6/12 pitch has a vertical rise of 6″ over a horizontal distance of 12″. Select the appropriate flashing.
- Determine the total length of chimney and stovepipe required for the installation. To calculate the installed per length of 5″-8″ DuraTech pipe, subtract 1 ¼” per joint. For 10″-24″ diameter, subtract ¾” per joint of pipe. Subtract 1 ¼” per joint of DuraBlack stovepipe. Subtract 1 ½” per joint of DVL stovepipe. Minimum chimney height, at sea level, of straight vertical chimney is 10′ to 15′ above the appliance outlet. Higher elevations, or the use of elbows or a tee, will require approximately 30% to 60% more height to provide for an adequate draft.
- For a UL approved shroud, see the DuraTech Shrouds Installation Instructions (L157). View online at www.duravent.com, under catalogs and instructions.
- Be fire safe. Maintain at least 2″ clearance to combustibles. Follow local building codes and have your chimney inspected by a certified professional.
- DuraTech® Instructions 5″-8″ (PDF, 1.7MB)
- DuraTech® Adjustable Length Installation Instruction Supplement (PDF, 673KB)
- DuraTech® Universal Support Installation Instruction Supplement (PDF, 698KB)
- DuraTech® Shroud Instructions (PDF, 434KB )
- DuraTech®: New Chimney Cap Assembly L1510 Installation Instruction Addendum (PDF, 445KB )
- DuraTech® Comparison (PDF, 589KB )
- Woodburning Best Practices (PDF, 391KB )
- Oil Sizing Chart (PDF, 122KB )
- DuraTech® 5”-8” Square Ceiling Support Box w/ Collar (PDF, 70KB )
- Black Paint (PDF, 889KB )
- DuraVent now offering DuraTech® Tee Cap (PDF, 458KB )
- DuraTech® Square Ceiling Support Box (PDF, 205KB )
- DuraTech® Adjustable Parts (PDF, 380KB )
- DuraTech® Snow Splitter (PDF, 161KB )
- DuraTech® Finishing Collar with Mechanical Connection (PDF, 196KB )
- DuraTech® for Oil (PDF, 186KB )
- DuraTech® Finishing Collar w/Adapter (PDF, 194KB )
- DuraPlus® & DuraTech® Support Boxes (PDF, 220KB )
- IHP High Efficiency Wood Fireplace Adapters(PDF, 106KB )
- IHP High Efficiency Wood Fireplace Adapters FR(PDF, 107KB )
- Do it Yurtself (PDF, 3.90MB)
- DuraTech® Flat Ceiling Support Boxes ( YouTube, 1:42)
- DuraTech® Spacer Tool for Locking Band ( YouTube, 2:06)
- Introduction to DuraTech® Support Boxes ( YouTube, 1:27)
- DuraTech® Vaulted Ceiling Support Boxes ( YouTube, 1:18)
- Tips and Tricks on How to Install and Clean Your Chimney’s Spark Arrestor ( YouTube, 2:02)
- DuraVent DoitYurtself ( YouTube, 0:47)